What Causes Hot Water to Smell Like Rotten Eggs
The most common cause of smelly water is anaerobic bacteria that exist in some water and react with sulfur and the magnesium and aluminum sacrificial anodes that come with most water heaters to produce hydrogen sulfide gas, making the classic rotten egg odor. The problem is most common in well systems, either private or municipal.
Softening can make smelly water much worse. By the way, don't blame the water heater manufacturers. It's not their fault and it's not their responsibility. It's just a condition that exists in some parts of the country and each person has to deal with it.What Not to Do to Get Rid of Smelly Water
We've heard of plumbers or handymen advising people to remove the sacrificial anodes from their water heaters as a solution to smelly water. It's a solution all right, but one that will ensure that your water heater rusts out in record time. There is a reason why removing an anode voids all the manufacturers' warranties.
Additionally, people have been told to replace a magnesium anode with an aluminum one. Don't. Aluminum causes just as many rotten eggs as magnesium.
Anodes for Smelly
Cheap, simple, effective, but not forever. Shut off the cold water valve to your water heater, open a hot faucet somewhere in your house to relieve pressure, drain some water from the tank, open the plumbing on one side, and dump in one pint of drugstore-type hydrogen peroxide per 20 gallons.
Close everything up, turn on the cold water again, and let some water run from all spigots and taps. You should be odor-free until the next time you go out of town and allow the water heater to sit unused. Then you'll have the problem again.
By the way: use peroxide, not chlorine bleach. Either will work, but peroxide is much safer.
One caveat: if you have smelly water at one sink, but not all of them, dump chlorine bleach down the basin overflow and drain. Sometimes bacteria can build up in there, too.
And apropos to that: make sure it's really the hot water that smells. There are places where there is so much sulfur in the water that hot AND cold water smell. Applying these procedures won't solve that. But if the water smells like rotten eggs, and you can smell it at every hot fixture, then these solutions will work.The Complete Fix, in Most Cases ...
Very often, replacing the standard magnesium or aluminum anode rod with an aluminum/zinc alloy anode will solve the problem. The zinc is a key ingredient, since pure aluminum anodes will also reek to high heaven. Also, some people use the terms aluminum and aluminum/zinc interchangeably. It's important to be specific or you won't solve the problem.
For most folks, an aluminum/zinc anode is the cheapest permanent fix for this problem and we suggest that you to try it first before considering the alternatives -- unless you soften your water. More on that in a moment.
Contrary to our usual advice, we do not think you should put two anodes in your tank, even aluminum/zinc ones, as it may worsen the odor.
These anodes come in four flavors: solid hex-head, flexible hex-head, solid combo, flexible combo. Those terms, doubtless, mean nothing to you, but they're important if you're to choose the right anode.
The photo at right shows combo and hex anodes. The former is also called an outlet anode.
Hex-heads go in their own port on top of the water heater. In some cases, you'll be able to see the hex head. If you can't, the anode is either hidden under the sheetmetal, or possibly under a plastic cap, or your tank has a combo anode. Look for the cap halfway between the edge and center of the top.
Combo anodes share the hot-water-outlet port. If you're not sure if there is an anode in there, you'll have to unscrew the nipple to see if there is an anode beneath it.
Some water heaters have two anodes. Not only is it important to put an aluminum/zinc anode into the heater; it's also important to remove all previous anodes or the hot water will still smell.
Solid hex-head anodes need 44 inches of overhead clearance. Solid combos need 48. Flexible anodes are loose links connected with flexible wire. They are good down to 12 inches overhead clearance, and can be cut shorter if they are too long for the tank.... But, If You Have Softened Water
We have had a few people buy an aluminum/zinc anode and the odor didn't go away. That's vexing for them and us. A few were in unsoftened water, but most involved softened water. Softening can speed up anode consumption by increasing the conductivity of the water. That can increase the amount of hydrogen sulfide gas produced.
Some of these people thought that the anode had some secret ingredient that had been used up. This is NOT the case. If one aluminum/zinc anode fails to solve odor issues, the next one won't do any better.
So we started offering powered anode rods. A sacrificial anode creates an electrical reaction inside a water heater as it corrodes. A powered anode does the same by feeding electricity into the tank. Since there is no magnesium or aluminum, there's no smell. We don't recommend them for everybody, though, because they're several times more expensive than sacrificial anodes. But they are permanent: they aren't sacrificial, so they don't need replacement.
Another important point: powered anodes are not odor-eaters. They merely function to protect a water heater without creating any odor. So No. 1, don't think it will fix anything other than rotten-egg odor. And No. 2, if you buy one without checking with us and still have odor, let us know and we'll troubleshoot and solve your problem. We've gotten pretty good at that.
One more thing: There are several configurations of residential water heaters. Most have a hex-head anode in its own port somewhere on the top of the tank. A few do not. Most of Bradford White's, and some of A.O. Smith's and State's residential tanks employ a combo anode/hot-water outlet/nipple in the hot port. A powered anode can be used with those tanks by adding a galvanized tee to the hot port. The bottom port of the tee will connect to the tank via a PEX-lined nipple; the plumbing to the building will go out the side port, also via a PEX-lined nipple; the powered anode will screw into the top port with the element hanging down inside the tank. It WILL be necessary to change plumbing that comes straight down, so that it enters the side, and there is no way to avoid that. SKU25 is the variant for that, and includes the extra parts and instructions.
The other variant, SKU27, is used in tanks with hex anodes. It includes parts to back the powered anode up off the surface of the heater because the cutout in the cover is narrower than the hex nut on the powered anode. Without them, people would have to enlarge the cutout with snips.
Why galvanized fittings and PEX-lined nipples instead of brass? Well, the powered anode hex nut is galvanized, so connecting it to brass could cause electrolysis problems, and if any sort of bare metal nipple were used and the electrode touched it, the anode would short-circuit and not protect the heater.
How do you tell if an anode is hex or combo? Best to tell us what you've got and let us help you figure that out. .
And worth mentioning again: Once in awhile aluminum/zinc anodes fail to resolve odor issues in unsoftened water, but mostly they work. It's a little bit of a gamble. We could tell everybody to buy a powered anode, but they're pricey. This is your choice, your gamble. Most people will win the bet, but it's your decision.Still, If You Have a Vacation Cabin...>
... When a heater sits idle a long time, stagnation odor can develop and it's different from anode odor and requires a different solution. Click here to learn about the Peroxide Fix.Issues With Aluminum
In other parts of our site, we warn of issues with aluminum anodes. Those issues are exactly the same with aluminum/zinc anodes, which are about 92 percent aluminum. So if you install an aluminum/zinc anode, get in the habit of running the cold water for a few seconds before drinking it or cooking with it. That will flush out any aluminum-laden water from the water heater that has cooled off in the piping since the last use.Finally, Before You Buy Anything
Here is a simple troubleshooting sequence:
1. What does it smell like? These products solve rotten-egg odor, but not all odors.
2. Does the cold water also smell? If so, is it as bad as the hot water or less so?
3. Where does it smell? Is it at all taps, or just some taps? If it's not everywhere, then it's not the water heater and doing something with the water heater is going to disappoint you. Often, though, in these cases, pouring chlorine bleach down the shower and sink drains and sink overflow will solve the problem. Also, read Water Heater Odor in Tanklets.
4. Are you using a water softener? If yes, then aluminum/zinc sacrificial anodes are probably not going to solve the problem. Think about a powered anode instead. They cost more, but they have an incredible success rate. It's also important to mention that the primary function of any anode is to protect a water heater from rusting and powered anodes do that in softened water very well. Odor or no odor, people with softeners should be using powered anodes or be checking their sacrificial ones yearly.Pricey Alternatives
There are a couple of other potential solutions you can consider. One is Rheem's Marathon electric heater, which is plastic-lined and has no anode. However, it costs several times more than a standard water heater and might be expensive to operate in some parts of the country where the utility rate structure favors gas.
Another is an instantaneous heater. We're not overly fond of those. They cost several times more than a tank-type heater and have their own problems. To see what we think is the downside, read Tankless. Still, this is one place where they might be a solution.Why Me, Oh Lord?
There have been a number of situations where people replaced their water heater and found they had smelly water with the new one even though they didn't with the old one. All we can do is speculate on the causes. All the action in water heaters takes place where nobody can see and it never happens in a scientific laboratory testing environment.
It might be that toward the end of the life of a water heater, there was too little anode left to make much hydrogen sulfide gas. Or it might be the water supply changed in some way. Our own water heater once had smelly water and required an aluminum/zinc anode, and now it doesn't.
There's something few realize: water is a chemical and one that is constantly changing. The water that flows out of the tap this evening may be different from that from this morning, either because of what's in the ground or because water companies have changed their sources of supply or added something new to it.Home | Site Map